|Condition:||Original New||Warranty:||12 Months|
|Shipping Term:||DHL/TNT/UPS/FEDEX Etc.||Package:||Original Package|
|Application:||Indusrial Ect||Input:||AC 100-240V|
Ironman Technology Co.,LTD
● HONEYWELL ● AB ● OMRON ●SIEMENS ●SCHNEIDER
● ROSEMOUNT● ABB ● NOTIFIER ●MTL ● GE ●And many more !
VE4050A1200T Solenoid gas Valves burner Honeywell new in box
Lead time:3-5 days
New with one year warranty
FEATURES • V4295A,S are used with 120 Vac controllers; V8295A,S are used with 24 Vac controllers. • Models available in Normally Closed and Normally Open configurations. • Normally Closed models, for safety shut-off applications, consist of a direct on/off operator for opening and closing of the valve. • Normally Open models, for vent (double block and bleed) valve applications, consist of a direct electric on/off operator for closing and opening of the valve. • Models are suitable for the control of gaseous fluids in gas consuming appliances according to international standards. • Models have 1/4 inch NPT inlet and outlet pressure taps. • Models have inlet screen to protect the valve from the entry of dirt.
APPLICATION The electrically operated V4295A, S and V8295A, S Solenoid Gas Valves control the flow of natural and LP (liquefied petroleum) gases. These valves are used on atmospheric boilers, commercial water heaters, roof-top make-up air burners, power burners and boilers.
SPECIFICATIONS Models V4295A Normally Closed (N.C.) Safety shut-off Valve, 120V V4295S Normally Open (N.O.) Vent Valve, 120V V8295A Normally Closed (N.C.) Safety shut-off Valve, 24V V8295S Normally Open (N.O.) Vent Valve, 24V Type of gas Air, Natural, Manufactured, Mixed and LP gas. Valve capacities Refer to Figures 1 and 2 Valve pattern Straight through, non-offset Body Material Die cast aluminum Electrical terminations Screw terminal connections Valve opening time Less than 1 second
INSTALLATION When installing this product... 1. Read this instructions carefully. Failure to follow them could damage the product or cause a hazardous condition. 2. Check the rating given in the instructions and on the product to make sure the product is suitable for your application. 3. Installer must be a trained, experienced, flame safeguard control technician. 4. After installation is complete, check out product operation as provided in these instructions.