|Condition:||Original New||Warranty:||12 Months|
|Shipping Term:||DHL/TNT/UPS/FEDEX Etc.||Name:||Honeywell Limit Switch|
|Feature:||Solid Material||Type:||Anti Corresion|
precision limit switch,
enclosed limit switch
Ironman Technology Co.,LTD
● HONEYWELL ● AB ● OMRON ●SIEMENS ●SCHNEIDER
● ROSEMOUNT● ABB ● NOTIFIER ●MTL ● GE ●And many more !
New C6097A2310 Honeywell Pressure Switch new in stock DHL shipping
Lead time:3-5 days
New with one year warranty
The gas pressure switch C6097A is used to detect the pressure of city gas, natural gas, LP gas or air etc. When the gas pressure changes, the diaphragm of the pressure receiving part detects it and operates the (SPOT) switch to ON/OFF control of the external electrical circuit. These switches are widely used to detect the upper limit or lower limit pressure of gas or air to be supplied to a gas burner, or to detect the clogging of the interlock filter of a burner blower
1. Read these instructions carefully. Failure to follow the instructions could damage the product or cause a hazardous condition. 2. Check the ratings given in the instructions and on the product to make sure the product is suitable for your application.
Accurate pressure set point adjustment (stand alone only) (tolerance <3% over total scale) 1. Remove the screw from the test nipple inlet. 2. Connect the tube of the pressure measurement device to the nipple (Fig. 1. F). 3. Remove the cover of the pressure switch. 4. Slowly release pressure of the main gas supply line until the desired value is reached. 5. Turn dial slowly until contact 1-3 opens and contact 2-3 closes. 6. Replace the cover. 7. Disconnect the pressure measurement device and replace the screw. Checkout Checking cut-off pressure After the installation is completed, continue with the following procedures: 1. Slowly close manual main valve with the burner in operation. Shut down should occur when the pressure drops below the set point and the alarm (if connected) should be energized. 2. Re open the manual main valve. The pressure should rise and exceed the set point value, the burner should start up and the alarm turn off after the reset button is depressed.
Contact Person: Sales Manager